On the progress of restoration work at the Sayano-Shushenskaya HPP as of 12.00 hours on 8 September, 2009
The flow sections of hydro-generator 2 and hydro-generator 6 have now been dried out. Work on identification of defects and restoration is being carried out on hydro-generators 6, 5, 4, 3 and 8. Installation of the metal structures of the support column in the turbine room near hydro-generator 2 has been completed, concrete is being laid and the roof at level 327.00 of hydro-generator 9 is now being dismantled.
Work is continuing to restore the electric power supply grid for the HPP’s own needs: two 35/6 kV substations with a capacity of 10 MVA and 3,125 MVA have been installed and connected, as have 6 kV busbars Sh1, Sh2 and Sh3 and 0.4 kV boards N1, N4, N9 and N17.
The systems for the station as a whole are being restored in accordance with the set timetable: Pump stations (artesian, drainage and sewage) have been started up, as has the hot water supply; the smoke-removal system is also now in operation in the installation site block. Preparations are under way to create additional entry routes to the construction zone of the turbine room from the right bank and installation has been started of a motor road flyover at the end of the turbine room block.
Within the scope of preparations for the winter season, creation of the thermal contour of the turbine room is also under way and it is planned to complete is by
Over 2125 people are currently involved in the accident and restoration work at the Sayano-Shushenskaya HPP, plus 50 pieces of equipment.
The inflow of water to the dam of the Sayano-Shushenskaya HPP is
At the Mainskaya HPP, hydro-units 1, 2 and 3, with an aggregate capacity of 193 MW, are in operation, the headrace level being 323.53 metres and with 4 of the spillway gates opened.
Constant environmental monitoring is being exercised over the state of the water in the
Shares / ADR